An air conditioner can collect a great deal of water while it is extracting moisture, or humidity, from the air inside of the residence. Regarding window air conditioners, the water collected in the course of regular running goes down the AC coil and drops into the base, and is then directed to the back. Most of the water is raised up by the fan blade and utilized to cool the heating coil, while most of it goes to the rear where it drains outside of the household. However, for the situations when water is leaking within ones home from a window AC unit, here are AC Repair Collierville TN’s ideas on ways to troubleshoot the problem.
Finding the source of a Collierville air conditioner leak can be difficult, for it can seem like it is coming from more than one location, and only happen occasionally. Below are a few recommendations for the most familiar explanations why water leaks could happen with an air conditioning unit.
1. Inaccurately installed
For window air conditioners, they need to be installed to ensure the back of the unit is a little bit lower than the front. Doing this permits the water being removed to drain to the back of the device. A level variation of one inch is effective. Test this initially. Water will run directly into the room and not outdoors if installed too low at the front.
2. Icing up
Water that is being removed from the air within the room can turn to ice if the AC is no longer working effectively. Take off the front grill while the unit is functioning to observe if ice is found. There are several factors this could happen and it will be best to call us to have a look at the AC unit.
3. Air leaks about air conditioner
If warm air from outside is allowed to enter indoors through around the air conditioner it will merge with the cooler, dryer indoor air. Condensation will take place when the 2 distinct temperature airs meet. If water is leaking from the front of the air conditioner check to observe whether it is dripping from the body of the machine, or if water droplets are attaching to the front. To evaluate this, operate the AC unit for thirty minutes then take a look at beneath the front edge of the base with a flashlight for water droplets. If water droplets are found, there is an air leak dilemma. By adding foam insulation about the unit prevents warm air from sneaking in.
4. Drain hole blockage
The backside of the air conditioner base contains a drain hole that enables water to drain. When it gets obstructed water can easily back up. To check, run the AC unit for A half-hour and then check to verify if it is draining appropriately. The base ought to hold a large quantity of water, but it shouldn’t be entirely full of water. If it looks clogged use a small piece of wood to unclog the drain hole.
5. Internal drains blockage
One can find tiny passageways that permit water to drain through the front of an AC unit to the back. Once they become obstructed, water will accumulate at the front of the unit and overflow. Should this happen, normally we will need to take out the air conditioner to service it. To check, run the device for A half-hour and then take off the front filter and plastic cowling. In the event the front of the base is totally full of water, but there exists only a little water leaking from rear of unit on the floor, there could be a clogged passageway.
6. Outside temperature is too cold
This dilemma is more usual around the end of the cooling period. When outdoor temperatures are under 60 degrees Fahrenheit in the evening the coil may possibly ice up. If one doesn’t observe any water leaks prior to going to bed, but there is water in front of the machine in the morning, this is likely the trouble. Merely shut off the AC unit prior to bedtime and only operate it as required in the day.